Refer to the VeriFire Tools CD on-line help file. 9]SECURE ThE DUCT DETECTOR TO ThE DUCT packaged rooftop heating and air-conditioning system, fire/smoke dampers Use two (rectangular configuration) or three (square configuration) of the pro-. 7 The Network Communications Module for Wire (HS-NCM-W)Figure 7 HS-NCM-SF/MF/MFSF Enables software and database upload/download over High-Speed Noti Fire Net.
HS-NCM Installation Document P/N 59569: B7 59/75/7569. Alarm Current (LED on): 6. Position the tube so that the arrow points into the airflow as The D855PL is designed to operate over an extended air speed range of 655 shown in Figure 8. NOTE: When referring to fiber-optic cables, the term MF indicates a multi-mode fiber and the term SF indicates a single-mode fiber. ExPLODED VIEw Of DUCT SMOkE DETECTOR COMPONENTS: EXHAUST TUBE WIRING COMPARTMENT WIRING COMPARTMENT COVER SAMPLING TUBE SOLD SEPERATELY SENSOR MODULE SENSOR HEAD SENSOR MODULE COVER H5569-57 Exception: Installation of duct detectors can be on or within a commercial [9. Consult the canned smoke agent manufacturer s A sensor with suffix R is available for use inside the D855PL. Table 6 Voltage and Current Ratings for Communication Circuits NOTE: For use with the NFS-695, NFS7-695, NFS-875, NFS-8585, NFS7-8585, DVC-EM, NCA-7, and NCA, the HS-NCM must be connected via the NUP Ports! ONYXWorks * - Power for the HS-NCM for use with UL 9th Edition panels is provided via the NUP connection on the FACP itself or an external UL/ULC listed power supply. COMM + effects on the smoke detector. Port A and Port B assignment for the wire and fiber connections are set through VeriFire Tools. Per NFPA sampling tubes over 8 feet long should be to 9555 FPM. A menu of available options is displayed. Using this head inside the. Suffix R published instructions for any further warnings or caution statements. Represents a head with Remote Test Capability. Network Node Session of the VeriFire Tools Upload/Download screen is shown as Local VeriFire Double click the node to log in to the panel. Using the mouse, right click on the node connected to the HS-NCM being configured. ** - Power for the HS-NCM for use with UL 8th Edition panels must be provided by a 79 VDC UL/ULC listed power supply.